Detailed description how to configure connection between Iconics Suite SCADA and iQ-R PLC controller using Melsoft Connection
Remember that your PC has to have the static IP address in the same subnet as PLC. iQ-R PLC default address is 192.168.3.39
iQ-R side configuration in GX works3
Open Your iQ-R project in GX Works3 to add new Melsoft Connection.
Go to the Navigation tree -> Parameter -> RxxCPU -> Module Parameter.
Then from the Module Parameter tab please open External Device Configuration -> Detailed Setting.
Drag and drop MELSOFT connection from Module List -> Ethernet Selection -> Ethernet Device (General) -> MELSOFT connection.
Save settings nad close window (Ethernet Configuration -> Close with Reflecting the setting)
Please don't forget to apply the settings.
Rebuild the project.
Send the project to the PLC.
Workbench (Iconics Suite) side connection.
In Workbench go to the Project Explorer : Data Connectivity -> Mitsubishi Electric -> Context Menu -> Network Discovery...
Click the Start Discovery button.
When finding a equipement end select which equipment you want to use in your project and click Import
Now find your device in the project tree and using context menu click Add Tag Group.
Name your tag group, add tags and remmeber to apply any changes.
Now, open the context menu on your device and click Activate Device.
The conncection is working and your tags are visible in GraphWorx64 and ready to use.
GraphWorx64 Data Browser view